Physical separation of the supply pipe by at least two pipe diameters (never less than one inch) vertically above the overflow rim of the receiving vessel. In this case line pressure is lost. Therefore, a booster pump is usually needed downstream, unless the flow of the water by gravity is sufficient for the water use. With an air gap there is no direct connection between the supply main and the equipment. An air gap may be used to protect against a contaminant or a pollutant, and will protect against both back-siphonage and backpressure. An air gap is the only acceptable means of protecting against lethal hazards.
Authorization Path: 18.104.22.168.17.0